Flexible gas pipe stainless Uniroll 10 mt. 3/4 "covered for gas UNI EN 15266tubo yellow coated for gas CSST UNI EN 15266 max 0.5bar. Corrugated formable pipe system PLT-CSST in AISI 316L stainless steel coated with yellow protective coating for the transport of gas according to UNI EN 15266 : 2007 - UNI / TS 11340. the "pipe system (kit)" PLT-CSST (corrugated stainless steel tubing STL) covered Uniroll of mbm is certified and conforms to European standard EN 15266: 2007 in all its components, requiring no intervention by the installer for the formation of the sealing bodies (flaring), as required in point 3.2 of the reference standards. It also complies with the technical specification UNI / TS 11340 relating to the installation of the CSST tube where in point 4.3. 4 it is required that the seal must be guaranteed metal on metal. The CSST tubes coated are suitable for the realization of installations for domestic and similar use, for users with single nominal thermal capacity not greater than 35kw that use gas of the first family (city gas), the second family (natural gas: methane) and third family (lPG). In the "naked" version, the tubes are suitable for the transport of drinking water, in accordance 'with the decree n ° 174 dated 06/04/2004. Assembly instructions valid for both coated tube that naked: Cut to the desired length and remove from both sides about 2.5 cm. the protective sheath when present. Enter the appropriate nut and place the grip preformed on the second wave of the corrugated tube. Bring the nut in contact with the grip preformed, insert the special metal seal. Connect to the plant or to a nipple with a flat abutment and tighten so that the deformation of the corrugated pipe folder face seal between the two rings. Use the supplied special adhesive tape resistant up to 105 ° c to seal the metal parts. To avoid corrosion and damage to form a double layer of the same. Certifications: The pipe system covered Uniroll of mbm is certified and complies with the UNI EN 15266: 2007 it establishes that all requirements for certification: design, materials, testing, manufacturing, marking. It is important to point out that "the whole" system conforms to the aforementioned reference standards, particularly in 3.2 where it is explicitly stated: "Collapsible tubes with their related components obtained or specified from a manufacturing source that has the responsibility to design and performance for the" performance kit that must therefore be ensured without the operator manually intervenes in the formation of the sealing members, for Therefore Uniroll is "autocartellante". The UNI EN 15266 also requires the manufacturer with a continuous control over entire production process, act to ensure the consistent quality of the product, mbm is also certified with the quality system iso: 9001. In the "naked" version, the tubes are suitable for the transport of drinking water, in accordance 'with the decree n ° 174 dated 06/04/2004. Statement and method 'installation there are different rules governing the design, installation, testing and maintenance of gas equipment for domestic and similar use, which must be made or modified in all the various phases in a secure and reliable, with primary emphasis on the safety of persons, animals and property, not to mention the protection of their environment, by qualified personnel with appropriate knowledge and experience. in the specific case of systems made with the system of pipes CSST Uniroll of mbm the main reference standards are the following: UNI EN 15266: 2007 and 'the product standard, which defines the parameters for designing the production, and the certification of 'entire CSST tube system. UNI / TS 11340.2009 and 'the standard installation, which, when applied in accordance with UNI 7129 and UNI 7131 establishes the mode of installation and use of the CSST tube systems. We would like to point out that the CSST tubes, being by definition "formable tubes", are not subject to the regulation UNI EN 14800, and can therefore have a length greater than 2 m. On completion of work, the installation company, after all the checks provided by law, must issue to the purchaser a declaration of conformity of the plant, citing the two previously named regulations. The CSST tubes covered for mbm Uniroll of the gas system can be installed with different modalities' of pose: a view, underground, concealed, in a raceway or niche, both inside and outside of uni or multi family buildings, following anyway all the criteria,
Registered users can share their experience with this product. Register to access all of the benefits reserved to registered users or click on login if you are already registered.